You can use the Instant Quote Tool, which gives you many options for your floor heating coverage. Use this interactive tool to design your room online and receive an instant quotation with product recommendations, rough-in and installation kits, cost of your control, etc. Planning your floor heating project is made easy when using our Instant Quote Tool.
Send us your floor plan or fax it to (800) 408-1100 and we will send you a quote, product recommendation and a free custom installation plan for your project.
Yes, but any furniture that may trap heat, such as pieces with an enclosed bottom, should be avoided. Furniture on legs with a clearance of at least 3" is permissible.
To prevent any overheating, we recommend that you do not install any electric radiant floor heating elements closer than 4" from the wax ring.
Please keep in mind that you must check your electric floor heating system with a digital ohmmeter in conjunction with a Circuit Check™. Take an initial reading as soon as you take the product out of the box to verify that it is within -5% / +10% of the values stated on the product’s label. This will give you a basis of comparison for future readings. Take a second reading once you have positioned the system to match your custom installation plan. It is also advisable to take an additional reading in the middle of the tile installation, just to make sure that the Circuit Check™ is doing its job. Then, take a final reading when you are finished with the floor installation and are ready to hook up the thermostat.
The Circuit Check™ is a tool developed by WarmlyYours to give you peace of mind and ensure trouble-free installations. Simply hook up the cold leads to the tool while you position the system to match your custom installation plan.
The Circuit Check™ will continuously monitor the continuity of the circuit during the installation of your system and during the installation of your flooring. The Circuit Check™ beeps immediately when a short in the system is detected, alerting you to a potentially damaged cable in the area you are working, before you lay the tile over the electric floor heating system. The WarmlyYours technical support team is available 24/7 to provide assistance if the alarm sounds, or if you would have any questions during your installation.
No, it is recommended that floor heating only be installed in the areas that you will walk on. Heat can become trapped if installed under objects that do not offer enough clearance for air to circulate (such as a washer or dryer).
The subfloor will need to be prepared as per the instructions of the self-leveling cement (SLC) used. Please note that most self-leveling products require the use of a primer as specified by the SLC company.
Yes, in most cases, an electric floor heating system can be effective as a primary heat source. However, our TempZone™ and Environ™ systems are most commonly used as a secondary heat source, providing floor-to-ceiling radiant heat to any room in your home where you desire more warmth and comfort.
If you are considering electric floor heating for an addition to your home, such as a sunroom where you have no other source of heat, WarmlyYours offers an innovative online tool which calculates approximate heat loss. This tool can help you to determine if a WarmlyYours’ electric radiant floor heating system will provide your desired comfort temperature throughout the year. You can access the Heat Loss Calculator or you can call us at (800) 875-5285 and a Customer Service Representative will make the calculation for you.
A floor heating system can work as a supplemental heating source and make the basement warmer. If more heat needs to be added to the room, you can experiment with setting the floor heating thermostat to higher temperatures.
Yes, our TempZone Heating Products can be used for heating luxury vinyl tile or luxury vinyl planks in any indoor application.
Since most Luxury Vinyl Tile (LVT) manufacturer's set a maximum temperature for radiant floor heating, the system should have little to no effect on the rubber/cork backing.
Pre-attached backing can act as an insulating layer though, meaning it can prevent the radiant heating from efficiently directing heat up through the floor. Please check with the manufacturer for the r-value of the product. Look for an assembled plank with an r-value of less than 1. The lower the r-value, the better!
The best way is to use our Radiant Floor Heating Quote Builder tool. It’s a great way to get an estimation by simply providing project information like room size and subfloor type.
The temperature of your floor can range anywhere between 75°F to 95°F. The floor's actual temperature will depend on a number of factors including the amount of heat loss that the room experiences as well as the room’s configuration. For instance, the warmth contained in a two story entry way would likely be less than that of a smaller, more enclosed area such as a bathroom. In a bathroom that is located on the second floor of your home or over another floor in your home that is typically heated, the temperature of your heated floor should easily reach a comfortable temperature of 85 degrees Fahrenheit, if the electric floor heating system is installed correctly. For the heat loss calculation for your specific room, you can access the Heat Loss Calculator or you can call us at (800) 875-5285 and a Customer Service Representative will make the calculation for you.
WarmlyYours nSpiration controls are equipped with an in-floor sensor to precisely control the floor's temperature to comply with the wood manufacturer's temperature recommendation.
This is stated in the Installation Manual of the LVT product when purchased. On average, this maximum temperature will fall between 80°F and 83°F. This number can then be used to program the thermostat during setup to set the floor's maximum temperature.
Typically, electric floor heating is used as a supplemental heat source but in some cases, it can be used as a primary heat source. Electric floor heating is more energy efficient, less prone to spreading dust and allergens, and easier to control from room to room. Air-based heating systems can be used for both heating and cooling and can be a good way to control air quality in the home with regular maintenance.
For a more in-depth answer to this question, check out Your ‘Cheat Sheet’ for Radiant Heat vs. Forced Air.
No. A bathroom floor would be installed in the same way. Our TempZone floor heating systems are wet-location listed and ideal for bathroom floors.
If the flooring manufacturer has a warranty for electric floor heating, it should not be adversely affected by shrinkage, expansion, or warping. Again, it will depend on the brand and construction of the product. Some manufacturers may place limitations on the maximum floor heating temperature. To minimize expansion and contraction, some Luxury Vinyl Tile companies require heating the flooring to a continuous heating level with "setback" temperatures (lower temperature settings during the day and overnight) kept to a minimum.
While radiant heating can affect the expansion and contraction of the floor, the most overlooked and important factor is the relative humidity in the space, so a humidifier or dehumidifier may be needed.
The height of the membrane itself is just about 1/4" (7/32").
Yes, Luxury Vinyl Tile (LVT) is typically installed over the embedded heating element using self-leveling cement (SLC). Many people choose to use SLC when installing tile over floor heating.
We do not suggest using thinset to encase the heating wires with LVT, as it is very difficult to get thinset completely flat.
No, most in-floor heating is designed to be added to new flooring. If you do have existing wood floors you would like to add radiant heating to - it is possible to do so with an under-joist heating system.
LVT (Luxury Vinyl Tile), WPC (Wood Plastic Composite), and Solid Core all fall into the category of "vinyl flooring." These vinyl flooring types can be rated for floor heating, but the application will completely depend on the manufacturer's guidelines.
Please look in the installation manual and warranty documents of the LVT, WPC, and Solid Core flooring product that you are interested in to see if and what types of heating are allowed.
As for a list of manufacturers of LVT, WPC, and Solid Core products providing a warranty for their products with radiant heat -- many do provide a warranty for their products when properly installed with floor heating. The list of these is ever-changing, so please be sure to check with the flooring manufacturer for current recommendations.
For best results, we recommend a 1”- 1.5” maximum distance between the heating cable and the top of the floor. Nailed down hardwood will require sleepers to run the cable safely between board nails. Be sure to use 3/8" to 3/4" of self-leveling cement to embed the heating element.
We suggest the heating product be embedded in a minimum of 3/8" of self-leveling cement (SLC). Always check with the manufacturer for specific recommendations.
We suggest removing SPC or WPC flooring before installing the floor heating system over it if possible. If that is not practical, use an underlayment designed specifically for covering these types of floors. Radiant heating can be used with many types of these floors, but check with the flooring manufacturer to confirm that it can be paired with these types of systems.
Typically, an uncoupling membrane like Prodeso will be best for this application because it can be paired with accessories to effectively waterproof the subfloor.
However, if you have a cement subfloor, then ThermalSheet synthetic cork is a good choice because of its high 1.5 R-value and moisture resistance.
There are heating systems designed for floating floors, such as our Environ system. However, the flooring must be rigid enough so it does not mold itself to the heating cables over time.
Check the flooring manufacturer's floor heating recommendations. In most cases, the heating system will need to be embedded beneath the flooring. Check for all "flatness" requirements for the flooring you choose. The flattest floors utilize self-leveling cement when installed correctly.
Yes, if the flooring manufacturer recommends this installation method. In most cases, the heating element will still need to be embedded in self-leveling cement before the flooring is installed.
This membrane provides many benefits including speedy installation, uncoupling, crack isolation, vapor management, and load distribution.
Everyone has their own comfortable temperature setting, but we typically find that our customers use their thermostats to set the "floor temperature" of the system in the 78°F - 84°F range.
Cork flooring can be used with floor heating if the r-value is under 1. You will need to find the r-value of the flooring you choose and let your account manager know during the design stage. Cork flooring should have a low r-value to minimize trapped heat.
We recommend verifying 3 things with the manufacturer of the flooring product to be heated;
1.) Is the flooring product compatible with electric floor heating?
2.) What is the maximum temperature the flooring product can withstand?
3.) What is the temperature set back recommendation of the flooring product?
The most common spacing is 3.75" (3 membrane nodules) between runs of heating cable. Occasionally, systems will be designed with 5" spacing (4 membrane nodules).
No, the tile floor should be installed at the same time as the embedding of the heating cable.
No, the Prodeso Cable Installation Membrane does NOT eliminate the need for movement joints, including perimeter joints, within the tiled surface.
A Warmly Yours indoor floor heating system should not be installed with a GFCI breaker because GFCI protection is built into the thermostat and power module. And while it's not always required, we strongly recommend a dedicated circuit for each thermostat and power module to limit the occurrence of ground fault nuisance tripping caused by multiple GFCI devices on a circuit. The amperage of a breaker would depend on the amp draw of the heating system. For example, a TempZone Flex Roll (which provides approximately 15 watts of energy output per square foot) that is providing 15 square feet of heating coverage will draw only 225 watts ( 1.9 Amps), so a 15 Amp circuit would suffice. Always size breakers according to your local Electrical Code requirements.
When WarmlyYours floor heating systems are being installed on a concrete slab, we strongly recommend adding a layer of insulation over the slab prior to installing the system. While our systems provide up to 25% more heating power per square foot than many of our competitors, the slab will always act as a "heat sink." Some of the heat that would otherwise be transferred to the flooring surface will remain in the slab, causing the floor’s surface temperature to be considerably lower. This is true with any floor warming system.
When installed on top of a concrete slab without insulation, it is generally accepted that a radiant floor heating system will take the chill away from the floor and provide a small amount of warmth. Adding insulation on top of the slab and beneath any floor heating system will allow a greater percentage of the heat generated to transfer to the flooring surface. This results in greater efficiency and therefore faster warm up times, higher expected surface temperatures and lower energy usage. The floor will have the capacity to warm to a comfortable temperature, and in some cases can be employed as the primary heat source for that room.
The recommended types of insulation are natural cork, insulated tile backer boards, and insulated underlayment, such as ThermalSheet synthetic cork.
An area where large furniture will cover the floor should have enough clearance underneath to allow air to circulate. Any areas where floor heat may be trapped (rugs, box bottom furniture), let your sales rep know so we can design an installation plan around these areas.