Free shipping for orders over $100. Coupon automatically applied at checkout.
Terms & Conditions
Free ground shipping for qualifying WarmlyYours orders over $100.
Excludes expedited shipping, freight shipping, oversized and custom items.
Shipping via ground or standard surface service by any offered carrier is included.
Offer valid on orders shipping to the 48 contiguous states in the U.S. and 8 of Canada's provinces (not valid for Newfoundland and Labrador or Prince Edward Island).
Cannot be combined with other offers or promotions.
Other restrictions may apply.
CAN PT ECONOMY UNIT INTERFACE WITH BMS? CAN IT COMMUNICATE WITH BACNET OR MODBUS?
CAN THE UNIT INTERFACE WITH BMS? CAN IT COMMUNICATE WITH BACNET OR MODBUS?
No, the PT Economy (FPT 130) provides a summary alarm via a dry contact relay. This relay is energized whenever the unit is powered. So, with power off the NC contact is closed, and the NO contact is open. When the unit is powered these are in the opposite state. A fault will de-energize the alarm relay and close the NC contact. This allows for a default, power loss alarm without power.