TempZone™ Flex Roll Installation Guide Part 3 - Ensuring A Good Installation
INSTALLING YOUR RADIANT FLOOR HEATING ROLL
As you're installing your radiant floor heating, you'll want to make sure you are completing each step correctly to avoid costly mistakes and prevent damage to the cable and mat system. Whether you're installing your TempZone™ heated floors in the standard or free form process, you'll need it to be cut precisely and placed in the right way. In video #3 in our Flex Roll Installation Guide series, our expert will show you how to guarantee a good flooring installation. To ensure your heating remains unharmed throughout the installation process, you may want to use a safety system with sounds and alarms that can be activated before wires are attached. If at any time you have issues during your TempZone™ radiant heated floor installation, contact WarmlyYours for additional heated floor assistance, or read the manual for help.
Marking the roll is advised to assist you in cutting at the correct locations on the heating roll. Laying the roll side-by-side using cuts and turns is what gives Warmly Yours heating rolls their flexibility. At this time additional ohms readings are recommended to make sure the integrity of the heating wire has not been compromised.
Although unusual, it is possible to damage the heating elements during installation. The safety siren is a tool used to warn the installer of a short or a break during installation by sounding this alarm. (alarm chirping) It can be tested by turning it to the on position before the wires are attached.
Afterwards, if you hear this alarm please refer to the troubleshooting section of your installation manual, or call the Warmly Yours 24 hour installation support line.