Are you considering installing heated concrete floors in your home? Even if you aren't building a new home, perhaps you're thinking about adding a sunroom or garage to your house. If you want to enjoy your sunroom in all four seasons, or comfortably enjoy the beauty of a trendy new polished, stamped or stained concrete floor, you'll appreciate radiant heating under foot.
With WarmlyYours' concrete heating cables and mats, you can design your concrete floors to be as warm and functional as they are attractive.
Provide us with a sketch of your room that includes dimensions and other relevant information and you’ll receive a free SmartPlan within one business day.
Electric in-floor heating systems generate an even heat throughout your home and will not disturb dust, reducing the chance of possible allergic reactions. What's more, radiant heated floors reduce noise levels and the amount of dry air in your home. There are other benefits to floor heating as well, including financial perks, as they are inexpensive to install and typically don't add more than a quarter to electric bills.
WarmlyYours provides free design services to make sure that customers purchase the heating system that best meets their project requirements. Depending on the floor type and the shape and size of a room's layout, the size and placement of heating mats will differ.
While WarmlyYours electric radiant floor heating systems are typically installed by your floor covering contractor, a licensed electrician is recommended for the final thermostat hook-up. With every quote, we provide an Installation Plan layout, together with an electrical plan that has all the info required for the electrician.
Our electric radiant floor heating systems have withstood rigorous safety testing and earned the UL listing. They produce much less EMF than common household appliances like your TV or vacuum cleaner. The EPRI (Electric Power Research Institute) tests all electrical devices and publishes the data. Many common household appliances are tested at a distance of 6 inches. The test results indicate that on average, the EMF emitted for the following appliances, measured in Milligauss (mG) units, is:
Vacuum Cleaner: 300 mG
Microwave: 200 mG
Portable Heater: 100 mG
Dishwasher: 20 mG
Washing Machine: 20 mG
WarmlyYours TempZone™ (Twin): 1.8 mG
You can use the Instant Quote Tool, which gives you many options for your floor heating coverage. Use this interactive tool to design your room online and receive an instant quotation with product recommendations, rough-in and installation kits, cost of your control, etc. Planning your floor heating project is made easy when using our Instant Quote Tool.
Send us your floor plan or fax it to (800) 408-1100 and we will send you a quote, product recommendation and a free custom installation plan for your project.
Sunrooms can be very cold during the winter months. While a furnace may push some warm air into the room, the large number of windows, exterior walls, and other causes of heat loss in a sunroom will typically keep it from having a comfortable temperature level. Floor heating and radiant panels will add radiant heat, which the human body absorbs faster than other forms of heat, to the room so that it feels warm even at lower temperatures.
Yes. Unlike the heating cable for electric floor heating, the cold lead wires can be trimmed.
Yes, but any furniture that may trap heat, such as pieces with an enclosed bottom, should be avoided. Furniture on legs with a clearance of at least 3" is permissible.
When installing electric floor heating over a concrete slab, an insulating underlayment like CeraZorb is highly recommended to ensure efficient operation, faster heating times and warmer floor temperatures.
No, it is recommended that floor heating only be installed in the areas that you will walk on. Heat can become trapped if installed under objects that do not offer enough clearance for air to circulate (such as a washer or dryer).
The amount of amperage draw depends upon how large the area is that you are heating. For coverage of areas less than 30 square feet, the system will draw less than 3 or 4 amps. If you have a larger area over 120 square feet of heated space, then you may need a larger breaker plus additional controls. No matter what the size of the area you choose to heat, we recommend a dedicated circuit for your electric radiant floor heating system.
Yes, our TempZone Heating Products can be used for heating luxury vinyl tile or luxury vinyl planks in any indoor application.
Electric-resistance heating cables and systems have no polarity. This includes all current WarmlyYours heating elements.
The breaker and wire sizes are selected based on the total amperage of the WarmlyYours heating system connected to a single thermostat. This information is on the WarmlyYours heating system's installation plan, electrical plan, or UL label. Based on guidelines from the National Electrical Code: loads up to 16 Amps may utilize 12 gauge wire with a 20-Amp breaker, and loads up to 12 Amps - 14 gauge wire with a 15-Amp breaker. Local code and/or other factors may change these guidelines.
Since most Luxury Vinyl Tile (LVT) manufacturer's set a maximum temperature for radiant floor heating, the system should have little to no effect on the rubber/cork backing.
Pre-attached backing can act as an insulating layer though, meaning it can prevent the radiant heating from efficiently directing heat up through the floor. Please check with the manufacturer for the r-value of the product. Look for an assembled plank with an r-value of less than 1. The lower the r-value, the better!
Supplemental heat can be addressed by changing the spacing on cable installs. Floor location in the house is very important when considering adding supplemental heating to a floor. For example: If heating a second story floor, over a heated space, cable at 4" spacing can be used. The same type of heating over an unheated space would probably be done with TempZone Flex Rolls or TempZone Cable at 3" spacing. All heating is considered supplemental unless a heat loss calculation is done.
This is stated in the Installation Manual of the LVT product when purchased. On average, this maximum temperature will fall between 80°F and 83°F. This number can then be used to program the thermostat during setup to set the floor's maximum temperature.
WarmlyYours nSpiration controls are equipped with an in-floor sensor to precisely control the floor's temperature to comply with the wood manufacturer's temperature recommendation.
Yes, Luxury Vinyl Tile (LVT) is typically installed over the embedded heating element using self-leveling cement (SLC). Many people choose to use SLC when installing tile over floor heating.
We do not suggest using thinset to encase the heating wires with LVT, as it is very difficult to get thinset completely flat.
One thermostat can control multiple heating mats/cables as long as all the elements are using less than 15 amps. For TempZone™ Flex Roll systems for example that would be maximum of 120 sq.ft. for 120V systems and 240 sq.ft. for 240V.
No, most in-floor heating is designed to be added to new flooring. If you do have existing wood floors you would like to add radiant heating to - it is possible to do so with an under-joist heating system.
Yes, we have TempZone Shower and Bench mats with sizes designed specifically for shower installation and they are wet location listed for for installing electric radiant floor heating to a shower.
If the flooring manufacturer has a warranty for electric floor heating, it should not be adversely affected by shrinkage, expansion, or warping. Again, it will depend on the brand and construction of the product. Some manufacturers may place limitations on the maximum floor heating temperature. To minimize expansion and contraction, some Luxury Vinyl Tile companies require heating the flooring to a continuous heating level with "setback" temperatures (lower temperature settings during the day and overnight) kept to a minimum.
While radiant heating can affect the expansion and contraction of the floor, the most overlooked and important factor is the relative humidity in the space, so a humidifier or dehumidifier may be needed.
No. A bathroom floor would be installed in the same way. Our TempZone floor heating systems are wet-location listed and ideal for bathroom floors.
LVT (Luxury Vinyl Tile), WPC (Wood Plastic Composite), and Solid Core all fall into the category of "vinyl flooring." These vinyl flooring types can be rated for floor heating, but the application will completely depend on the manufacturer's guidelines.
Please look in the installation manual and warranty documents of the LVT, WPC, and Solid Core flooring product that you are interested in to see if and what types of heating are allowed.
As for a list of manufacturers of LVT, WPC, and Solid Core products providing a warranty for their products with radiant heat -- many do provide a warranty for their products when properly installed with floor heating. The list of these is ever-changing, so please be sure to check with the flooring manufacturer for current recommendations.
For best results, we recommend a 1”- 1.5” maximum distance between the heating cable and the top of the floor. Nailed down hardwood will require sleepers to run the cable safely between board nails. Be sure to use 3/8" to 3/4" of self-leveling cement to embed the heating element.
Floor heating will typically add the most heat to supplement an existing heating source and it will not take any extra space since it is embedded in the floor. If you are not remodeling your floors but have some open wall space, you should mount a radiant panel. For the most effective results, install the panel so that it points toward the area where you will spend most of the time.
Yes, with our programmable thermostats, you can choose which days and times the floor heating turns on for your comfort. With a Smart thermostat, you can also control these options from your phone while away from home.
We recommend verifying 3 things with the manufacturer of the flooring product to be heated;
1.) Is the flooring product compatible with electric floor heating?
2.) What is the maximum temperature the flooring product can withstand?
3.) What is the temperature set back recommendation of the flooring product?
82°F - 85°F is the most common comfortable warm temperature of the floor.
We usually recommend that you have an individual thermostat for each room. However, if it's an open floor plan and your local electrical code allows you to have one controller for the whole area, then it's definitely possible to have it all controlled from one thermostat.
The requirements are: 20 watts per square foot foot (with 3" spacing) without a floor covering; or 15 watts per square foot (with 5" spacing of cable only) with a floor covering. To calculate your exact power requirements, multiply the square feet by 20 or 15, as listed above and then divide by the voltage (120V or 240V) to arrive at Amps.
The cost for the heating elements in a Slab Heating system is $7 per sq. ft. ($8 CAD) for Slab Heating Mats and $7 per sq. ft. ($9 CAD) for Slab Heating Cables.
Everyone has their own comfortable temperature setting, but we typically find that our customers use their thermostats to set the "floor temperature" of the system in the 78°F - 84°F range.
Yes, sunrooms can be used in the winter, just activate your floor heating or radiant panel and turn your sunroom into a 4-season room. You will notice a tremendous difference in the room comfort, especially with the thermostat set to maintain a desired ambient temperature. WarmlyYours thermostats will do the work for you by energizing the floor for longer cycles.
Yes, if the flooring manufacturer recommends this installation method. In most cases, the heating element will still need to be embedded in self-leveling cement before the flooring is installed.
There are heating systems designed for floating floors, such as our Environ system. However, the flooring must be rigid enough so it does not mold itself to the heating cables over time.
Check the flooring manufacturer's floor heating recommendations. In most cases, the heating system will need to be embedded beneath the flooring. Check for all "flatness" requirements for the flooring you choose. The flattest floors utilize self-leveling cement when installed correctly.
You should install the cable 2-3" below the finished surface, and attach it to rebar and/or reinforcing wire mesh to secure the cable in place.
The slab heating cable sits in the middle of concrete pour. Here are the layers for this application from bottom to top:
The layers for the full installation are as follows:
Call tech support at (800) 875-5285 to customize this to your unique application.
In-stock items will ship the same day if you place your order before 4:00 PM CST.
Stop installation, box out a 3"×3" area surrounding the damaged area and call tech support at (800) 875-5285.
Any trade professional is qualified to layout cables and/or mats; electricians must make the electrical connections and test the wire; you can hire a concrete contractor to install the concrete for you.
Yes, we offer several options to help make your floor heating system water resistant or waterproof. Our TempZone product line is designed for wet areas - making it completely safe for rooms that will have water on the floor at times or may experience leaks or flooding. We also offer waterproofing bands for our TempZone Cable + Prodeso Uncoupling Membrane system. Allowing you to waterproof all seams and the perimeters of the wall - guaranteeing that your floor heating system stays safe and prevents water from leaking to areas below.